Standard Interpretations - Table of Contents|
| Standard Number:||1910.178|
May 24, 1995
Mr. E. C. Arms, Jr.
Westvaco Box 70848
Charleston Heights, SC 29415-0848
Dear Mr. Arms:
Your letter dated January 31, 1994 to the Occupational Safety and Health Administration (OSHA) Dallas Regional Office requesting clarification of the use of powered industrial trucks in Class I, Division 2, Group C locations was transferred to the Directorate of Compliance Programs for response. I apologize for the delay in responding to your inquiry.
29 CFR 1910.178(c), Designated locations, was adopted from NFPA No. 505-1969, Powered Industrial Trucks. Table N-1 of 1910.178, Summary Table on Use of Industrial Trucks in Various Locations, does not list any trucks authorized for use in a Class I, Group C, Division 1 or 2 location. Therefore, your interpretation of Table N-1 of 1910.178 is correct.
Table 1-5 of NFPA No. 505-1992, Summary Table on Use of Powered Industrial Trucks, also does not list any trucks authorized for use in a Class I, Group C, Division 1 or 2 location. As indicated in your letter, the Class I, Group C, Division 2 location in Table 1-5 has table symbols under trucks designated as Type DS, DY, ES, EE, EX, GS, LPS, and GS/LPS which indicate "Type truck authorized to be determined by the authority having jurisdiction."
Although OSHA has not adopted NFPA No. 505-1992, please be advised that OSHA will accept compliance with Table 1-5 of NFPA No. 505-1992, only when it indicates "Type truck authorized in location described."
Therefore, OSHA will accept the use of powered industrial trucks that indicate "Type of truck authorized" in Table N-1 of 1910.178 and later versions of Summary Tables of NFPA No. 505.
OSHA will accept the use of a powered industrial truck that is listed or approved for fire safety purposes for the intended use by an OSHA accepted Nationally Recognized Testing Laboratory (NRTL), using nationally recognized testing standards. In addition, approved trucks must bear a label indicating approval by the testing laboratory.
Specifically, Section 1910.307(b), Electrical Installations, requ